|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015, CE, TUV, BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||20 working days|
|Payment Terms:||L/C, T/T|
|Supply Ability:||50 Sets per month|
|Product Name:||1650KVA Diesel Generator||Color:||Green|
|Cylinder No.:||12V||Cooling Type:||Water Cooled|
|Fuel Injection:||Electronic||Engine Brand:||Yuchai|
|Alternator Brand:||Faraday||Control Panel:||Smartgen HGM6110N|
3 phase standby generator,
diesel standby generator
1200KW / 1500KVA Prime Rating 3 Phase Diesel Generator With Yuchai Engine
Operating conditions of generator set:
1. Altitude: ≤1500 m.
2. Ambient Temperature: -15℃~50℃.
3. Relative air humidity: ≤90%.
4. The site can't has electric conduction dust and corrosive gas that destroies metal insulation.
5. The site can't has explosion danger.
Generaor Set Specifications:
|Dimension (L×W×H) (mm)||5560×2330×2670|
|Genset weight (kg)||12000|
|Number of Cylinders||12|
|Cylinder Arrangement||60º Vee form|
|Aspiration||Turbocharged after water-cooled|
|Bore×Stroke (mm)||200 x 210|
|Speed Stability (%)||≤5%|
|Lube Oil Capacity (L)||280|
|Fuel Consumption at 100% Load (g/kw.h)||≤195|
|Starting Method||DC 24V Electrical starting|
|Excite type||Brushless self-excited AVR regulation|
|Connecting type||3 phase 4 pole|
|Steady frequency change||0.50%|
|No load voltage||≥95%-105%|
|Insulation class||Class H|
Key start / auto start
Monitoring meters: Current; Frequency; Wire Voltage; Genset KVA; Genset KW; Output
Capacity; Output KW.H; Power Factor.Warning/Shutdown: Alternator Under/Over Volts, Frequency; Under/Over Speed; Low Oil Pressure; High Engine Temp; High/Low Battery Volts; Over Current; Earth Fault Shutdown.
INSPECTION AND TEST
1.1 Each engine shall be tested at manufacturer’s workshop to certify the engine output and fuel consumption in accordance with the site operating condition specified by purchaser on the specification datasheet.
1.2 All relevant information drawings pertinent to the testing and test procedure shall be transmitted to the purchaser in advance of the test date notification.
1.3 The purchaser shall call for additional testing if test results are unsatisfactory or marginal. Any equipment rejected shall be repaired or replaced to the purchaser’s satisfaction and tests shall be repeated.
1.4 Any unsatisfactory material, equipment, installation, or workmanship shall be replaced or repaired to the purchasers satisfaction at the manufacturer’s cost.
1.5 The engine and generator shall be tested individually in accordance with relevant standards specified above.
1.6 The completed and individually tested engine and generator shall be assembled onto the base plate with all auxiliaries, instruments and controls for a complete test of the generator set.
Guangdong Sunkings Electric Co., Ltd. Can provide professional OEM Service for customers.
1. Unique design and manufacture of generator according to customer’s requirement.
2. Customer logo printing or painting on the genset.
3. Installation and Operation manual neutral or headings can be design according to customer’s requirement.
4. Full warranty cover to support the customers.