|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015 , CE , TUV , BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||20 working days|
|Payment Terms:||L/C, T/T|
|Supply Ability:||30 Sets per month|
|Product Name:||1000KW Cummins Generator||Color:||Green|
|Cooling Type:||Water Cooled||Cylinder No.:||16V|
|Starting Method:||Electrical Start By 24V Batteries||Control Panel:||Deep Sea 6020|
containerized diesel generator sets,
container type generator
1250KVA Industrial Diesel Generators Cummins Power KTA50-G3
|Product Name||1250KVA Diesel Genset||Model||SCS1375B|
|Rated Power||1000KW / 1250KVA||Standby Power||1100KW / 1375KVA|
|Engine Brand||CUMMINS||Alternator Brand||STAMFORD|
|Dimension||5800×2280×2500 mm||Weight||11040 KG|
|Number of Cylinders||16|
|Cylinder Arrangement||60º Vee form|
|Aspiration||Turbocharged and air-to-air intercooled|
|Bore×Stroke(mm)||159 x 159|
|Speed Governor||EFC speed governor|
|Cooling System||Closed cycle water-cooled with fan drived by belt|
|Speed Stability (%)||≤5%|
|Total Lubrication System Capacity (L)||151|
|Fuel Consumption at 100% Load||199 g/kw.h|
|Starting Method||DC 24V Electrical starting|
|Number of Phase||3|
|Connecting Type||3 Phase and 4 Wires|
|Number of Bearing||1|
|Exciter Type||Brushless ,Self-excited, AVR automatic voltage regulation|
|Telephone Influence Factor (TIF)||≤50|
|Voltage Regulation, Steady State||≤±1%|
|Transient State Voltage||≤-15%~+20%|
INSPECTION AND TEST
1.1 Each engine shall be tested at manufacturer’s workshop to certify the engine output and fuel consumption in accordance with the site operating condition specified by purchaser on the specification datasheet.
1.2 All relevant information drawings pertinent to the testing and test procedure shall be transmitted to the purchaser in advance of the test date notification.
1.3 The purchaser shall call for additional testing if test results are unsatisfactory or marginal. Any equipment rejected shall be repaired or replaced to the purchaser’s satisfaction and tests shall be repeated.
1.4 Any unsatisfactory material, equipment, installation, or workmanship shall be replaced or repaired to the purchasers satisfaction at the manufacturers cost.
1.5 The engine and generator shall be tested individually in accordance with relevant standards specified above.
1.6 The completed and individually tested engine and generator shall be assembled onto the base plate with all auxiliaries, instruments and controls for a complete test of the generator set.
QUALITY CONTROL & WARRANTY
All generator sets should go through the rigorous testing before being released to the market place, including 50% load, 75% load, 100% load , 110% load and all protection functions (overspeed stop, high water temperature, low oil pressure and battery charging fail)
Our factory warrants that the gensets will be free from defects in materials and workmanship for a period of one year from the date of shipment or 1200 hours, whichever comes first. If the product proves defective during the warranty period,our factory, at its option, will:
(1) repair the product by means of telephone support or depot service at no charge for parts or labor,
(2) provide the new spare parts to replace the broken one for maintenance.