|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015, CE, TUV, BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||20 working days|
|Payment Terms:||100% L/C at Sight, T/T|
|Supply Ability:||80 Sets per month|
|Product:||Open Type||Cooling Method:||Water Cooled|
|Speed Governing:||Electronic||Starting Method:||Electrical Start By 24V Batteries|
|Engine:||Cummins / Perkins / China Brands||Alternator:||Stamford / Marathon / Faraday And China Brands|
emergency backup generator,
open type genset
50Hz Frequency and AC Three Phase Output Type Open Electricity Generating system
|Genset rated power||480KW/600KVA|
|Rated voltage||400/230V (adjustable)|
|Power factor||0.8 Lagging|
|Connecting type||3 phase 4 wire|
|Cooling system||Closed cycle water-cooled with fan, water tank|
|Overall dimension (L×W×H) mm||3300×1250×1850|
|Gross weight (kg)||5000|
|Engine type||6 cylinders in Line,4 stroke, direct injection|
|Aspiration||Turbocharged and air-to-air aftercooled|
|Rotating speed||1500 RPM|
|Engine cooling system||Water-cooled|
|Speed governing system||Electronic speed governor|
|Starting method||By 24V batteries|
|Engine filter system||Dry type air filter ,fuel filter, oil filter, water filter|
|Compression ratio||13.9: 1|
|100% Load fuel consumption (l/h)||≤95.1|
|Excite type||Brushless self-excited AVR regulation|
|Connecting type||3 phase 4 pole|
|Steady frequency change||0.50%|
|No load voltage||≥95%-105%|
|Insulation class||Class H|
INSPECTION AND TEST
1.1 Each engine shall be tested at manufacturer’s workshop to certify the engine output and fuel consumption in accordance with the site operating condition specified by purchaser on the specification datasheet.
1.2 All relevant information drawings pertinent to the testing and test procedure shall be transmitted to the purchaser in advance of the test date notification.
1.3 The purchaser shall call for additional testing if test results are unsatisfactory or marginal. Any equipment rejected shall be repaired or replaced to the purchaser’s satisfaction and tests shall be repeated.
1.4 Any unsatisfactory material, equipment, installation, or workmanship shall be replaced or repaired to the purchasers satisfaction at the manufacturers cost.
1.5 The engine and generator shall be tested individually in accordance with relevant standards specified above.
1.6 The completed and individually tested engine and generator shall be assembled onto the base plate with all auxiliaries, instruments and controls for a complete test of the generator set.