|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015, CE, TUV, BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||15 working days|
|Payment Terms:||L/C, T/T|
|Supply Ability:||100 Sets per month|
|Product Name:||63KVA Perkins Generator||Color:||White|
|Speed Governing:||Mechanic||Engine Brand:||Perkins|
|Alternator Brand:||Engga||Control Panel:||HGM6110|
Perkins 50KW / 63KVA Home Diesel Generator , Diesel Powered Generator
Detailed Product Description
Perkins 50KW / 63KVA Silent Diesel Generator Home Use Generator Set
Genset Data: 400/230V, 50Hz, 3 Phase 4 Pole, 1500RPM, Power Factor 0.8.
SHX Soundproof Generator Set Features:
|Genset rated power||50KW/62.5KVA|
|Rated voltage||230/400V (adjustable)|
|Rated current||90 Amp|
|Power factor||0.8 Lagging|
|Connecting type||3 phase 4 wire|
|Cooling system||Closed cycle water-cooled with fan, water tank|
|Overall dimension (L×W×H) mm||2600×1000×1400|
|Gross weight (kg)||1200|
|Engine structure||4 cylinders vertical in line,4 stroke, turbocharged|
|Rotating speed||1500 RPM|
|Engine cooling method||Water-cooled|
|Speed governing system||Mechanic speed governor|
|Starting method||By 12V batteries|
|Engine filter system||Dry type air filter ,fuel filter, oil filter, water filter|
|Compression ratio||17.25: 1|
|100% Load fuel consumption (litre/h)||≤12.2|
|Excite type||Brushless self-excited AVR regulation|
|Connecting type||3 phase 4 pole|
|Steady frequency change||0.50%|
|No load voltage||≥95%-105%|
|Insulation class||Class H|
INSPECTION AND TEST
1.1 Each engine shall be tested at manufacturer’s workshop to certify the engine output and fuel consumption in accordance with the site operating condition specified by purchaser on the specification datasheet.
1.2 All relevant information drawings pertinent to the testing and test procedure shall be transmitted to the purchaser in advance of the test date notification.
1.3 The purchaser shall call for additional testing if test results are unsatisfactory or marginal. Any equipment rejected shall be repaired or replaced to the purchaser’s satisfaction and tests shall be repeated.
1.4 Any unsatisfactory material, equipment, installation, or workmanship shall be replaced or repaired to the purchasers satisfaction at the manufacturers cost.
1.5 The engine and generator shall be tested individually in accordance with relevant standards specified above.
1.6 The completed and individually tested engine and generator shall be assembled onto the base plate with all auxiliaries, instruments and controls for a complete test of the generator set.
Introduction of Diesel Generator:
A Diesel Generator (DG) is a combination of diesel engine with electrical generator (often called an alternator) to generate electricity. DG sets are used in places that have no connection to power grid, and as emergency power-supply if the grid fails. In other words, DG sets remain the number one choice for standby and emergency power systems. DG sets are selected based on the electrical load they are intended to supply.