|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015, CE, TUV, BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||30 working days|
|Payment Terms:||L/C, T/T|
|Supply Ability:||5 Sets per month|
|Cylinder No.:||12V||Alternator:||100% Copper Wires|
|Starting Method:||Electrical Start By 24V Batteries||Engine Brand:||Cummins|
|Alternator Brand:||Stamford||Control Mode:||Manual/auto|
containerized diesel generator sets,
container type generator
1000KVA Containerized Diesel Generators Cummins KTA38-G5 Generator Set Power Generation
|Genset rated power||1000KVA/800KW|
|Rated voltage||400/230V (adjustable)|
|Rated current||1440 Amps|
|Power factor||0.8 Lagging|
|Connecting type||3 phase 4 wire|
|Cooling system||Closed cycle water-cooled with fan, water tank|
|Overall dimension (L×W×H) mm||6058×2438×2591|
|Gross weight (kg)||10200|
|Engine type||12 cylinders in Vee form,4 stroke, direct injection|
|Aspiration||Turbocharged and water-to-air aftercooled|
|Rotating speed||1500 RPM|
|Engine cooling system||Water-cooled|
|Speed governing system||Electronic speed governor|
|Starting method||By 24V batteries|
|Engine filter system||Dry type air filter ,fuel filter, oil filter, water filter|
|Compression ratio||13.9: 1|
|100% Load fuel consumption (g/kw.h)||≤196|
|Excite type||Brushless self-excited AVR regulation|
|Connecting type||3 phase 4 pole|
|Steady frequency change||0.50%|
|No load voltage||≥95%-105%|
|Insulation class||Class H|
Key start / auto start
Monitoring meters: Current; Frequency; Wire Voltage; Genset KVA; Genset KW; Output
Capacity; Output KW.H; Power Factor.
Warning/Shutdown: Alternator Under/Over Volts, Frequency; Under/Over Speed; Low Oil Pressure; High Engine Temp; High/Low Battery Volts; Over Current; Earth Fault Shutdown.
SCOPE OF SUPPLY
1. DIESEL ENGINE
1.1 Engine which includes wet type cylinder, direct injection combustion chamber, exhaust turbocharger, water cooling, electronic governor, etc.
1.2 Fuel system, which includes, fuel pump, strainers or filters, etc.
1.3 Air intake and exhaust system, which includes air filter, exhaust silencer, bellow, all intake and exhaust piping, cablings, instruments, valves and settings, etc.
1.4 Cooling system, which includes radiator with water level alarm and indicator, thermostatic switch, thermostatic heater, engine shaft mounted fan, all interconnecting piping, cablings, instruments, valves and settings, etc.
1.5 Lubricating system includes pumps, oil sumps, oil strainers and filters, all interconnecting piping, instruments, valves and settings, etc.
1.6 Starting system, which includes 2 sets of batteries, a set of AC charger, and interconnecting piping, cablings, instrument, valves and settings, etc.
2. AC SYNCHRONOUS GENERATOR
2.1 Generator, which includes exciter, rectifier, AVR, shaft mounted fan if required.
2.2 All interconnecting piping, cablings, instruments, valves and settings, etc.
3. COUPLINGS AND GUARD
3.2 Coupling Guard
4. CONTROL PANEL
4.1 Local automatic control panel
5.1 Common base plate
6.1 Generator Set Installation Manual
6.2 Generator Set Operation and Maintenance Manual
6.3 Generator Set Control Panel Manual
6.4 Engine Manual and Quality File
6.5 Alternator Manual and Quality File
6.6 Factory Acceptant Test Report
6.7 Relative Drawings and Diagrams