|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015, CE, TUV, BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||20 working days|
|Payment Terms:||L/C, T/T|
|Supply Ability:||100 Sets per month|
|Product Name:||63KVA Diesel Generator||Color:||Green|
|Cylinder No.:||4L||Air Intake:||Turbocharged|
|Alternator Brand:||Engga||Control Mode:||Auto/man|
Generator Cummins Diesel By Cummins Engine 63KVA 1500RPM Diesel Genset
Detailed Product Description
Genset Data: 415/240V, 50Hz, 3 Phase 4 Pole, 1500RPM, Power Factor 0.8.
1. Prime power 63KVA, standby power 70KVA.
2. Powered by Cummins engine.
3. Original Engga alternator.
4. Delixi air breaker.
5. Electric start with batteries.
6. Smartgen controller.
7. ATS is for option.
|Genset rated power||50KW/63KVA|
|Rated voltage||240/415V (adjustable)|
|Rated current||88 Amp|
|Power factor||0.8 Lagging|
|Connecting type||3 phase 4 wire|
|Cooling system||Closed cycle water-cooled with fan, water tank|
|Overall dimension (L×W×H) mm||1900×740×1250|
|Gross weight (kg)||860|
|Engine structure||4 cylinders vertical in line,4 stroke, turbocharged|
|Rotating speed||1500 RPM|
|Engine cooling method||Water-cooled|
|Speed governing system||Electronic speed governor|
|Starting method||By 24V batteries|
|Engine filter system||Dry type air filter ,fuel filter, oil filter, water filter|
|Compression ratio||16.5: 1|
|100% Load fuel consumption (litre/h)||≤12.7|
|Excite type||Brushless self-excited AVR regulation|
|Connecting type||3 phase 4 pole|
|Steady frequency change||0.50%|
|No load voltage||≥95%-105%|
|Insulation class||Class H|
Introduction of Diesel Generator:
A Diesel Generator (DG) is a combination of diesel engine with electrical generator (often called an alternator) to generate electricity. DG sets are used in places that have no connection to power grid, and as emergency power-supply if the grid fails. In other words, DG sets remain the number one choice for standby and emergency power systems. DG sets are selected based on the electrical load they are intended to supply.
SCOPE OF SUPPLY
1. DIESEL ENGINE
1.1 Engine which includes wet type cylinder, direct injection combustion chamber, exhaust turbocharger, water cooling, electronic governor, etc.
1.2 Fuel system, which includes, fuel pump, strainers or filters, etc.
1.3 Air intake and exhaust system, which includes air filter, exhaust silencer, bellow, all intake and exhaust piping, cablings, instruments, valves and settings, etc.
1.4 Cooling system, which includes radiator with water level alarm and indicator, thermostatic switch, thermostatic heater, engine shaft mounted fan, all interconnecting piping, cablings, instruments, valves and settings, etc.
1.5 Lubricating system includes pumps, oil sumps, oil strainers and filters, all interconnecting piping, instruments, valves and settings, etc.
1.6 Starting system, which includes 2 sets of batteries, a set of AC charger, and interconnecting piping, cablings, instrument, valves and settings, etc.
2. AC SYNCHRONOUS GENERATOR
2.1 Generator, which includes exciter, rectifier, AVR, shaft mounted fan if required.
2.2 All interconnecting piping, cablings, instruments, valves and settings, etc.
3. COUPLINGS AND GUARD
3.2 Coupling Guard
4. CONTROL PANEL
4.1 Local automatic control panel
5.1 Common base plate
6.1 Generator Set Installation Manual
6.2 Generator Set Operation and Maintenance Manual
6.3 Generator Set Control Panel Manual
6.4 Engine Manual and Quality File
6.5 Alternator Manual and Quality File
6.6 Factory Acceptant Test Report