|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015, CE, TUV, BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||15 working days|
|Supply Ability:||50 sets per month|
|Product Name:||1600Amp Synchronous Control Panel||Color:||White|
|Switch Brand:||Jingyi||Application:||Two Generator Sets|
|Width:||0.8 M||Control Function:||Automatic|
1600 Amp Diesel Generator Synchronization Panels For Two 800KVA Diesel Generators
Descriptions Of Control Panel Smartgen HGM9510
HGM9510 controller is designed for manual/auto parallel system generators with similar or different capacity. Additionally, it is suitable for single unit constant power output and mains paralleling. It allows automatic start/stop, parallel running, data measurement, alarm protection as well as remote control, remote measurement and remote communication function. It fit with LCD display, optional Chinese, English and other languages interface, and it is reliable and easy to use.
PERFORMANCE AND CHARACTERISTICS
With ARM-based 32-bit SCM, high integration of hardware and more reliable;
480x272 LCD with backlight, multilingual interface (including English, Chinese or other languages) which can be chosen at the site, making commissioning convenient for factory personnel;
Improved LCD wear-resistance and scratch resistance due to hard screen acrylic;
Silicon panel and pushbuttons for better operation in high/low temperature environment;
RS485 communication port enable remote control, remote measuring, remote communication via ModBus protocol.
Fitted with CANBUS port and can communicate with J1939 genset. Not only can you monitoring frequently-used data (such as water temperature, oil pressure, engine speed, fuel consumption and so on) of ECU machine, but also control start, stop, raising speed and speed droop via CANBUS port.
Suitable for 3-phase 4-wire, 3-phase 3-wire, single phase 2-wire, and 2-phase 3-wire systems with voltage 120/240V and frequency 50/60Hz;
Collects and shows 3-phase voltage, current, power parameter and frequency of Bus/mains.
For Bus, controller has loss of phase and phase sequence wrong detection functions; For generator, controller has over voltage, under voltage, over frequency, under frequency, over current, over power, reverse power, loss of phase, phase sequence wrong detection functions;
Synchronization parameters:Voltage Difference Between Bus and Mains, Frequency Difference Between Bus and Mains, Phase Difference Between Bus and mains;
Finished synchronous control system for two units of generator sets