|Place of Origin:||Foshan, China|
|Certification:||ISO9001:2015, CE, TUV, BV|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Standard export packing|
|Delivery Time:||20 working days|
|Payment Terms:||L/C, T/T|
|Supply Ability:||50 Sets per month|
|Product Name:||900KVA Standby Generator||Color:||Green|
|Cylinder No.:||12V||Cooling Type:||Water Cooled|
|Starting Method:||Electrical Start||Engine Brand:||Cummins|
|Alternator Brand:||Engga||Control Panel:||Deep Sea|
Water Cooled Generator 900KVA Cummins KTA38-G2A , Cummins Standby Generator
The Components Of Genset:
Generaor Set Specifications:
|Dimension (L×W×H) (mm)||4100×1800×2500|
|Genset weight (kg)||7500|
|Number of Cylinders||12|
|Cylinder Arrangement||60º Vee form|
|Aspiration||Turbocharged after water-cooled|
|Bore×Stroke(mm)||159 x 159|
|Speed Governor||EFC speed governor|
|Speed Stability (%)||≤5%|
|Total Lubrication System Capacity (L)||114|
|Fuel Consumption at 100% Load||202g/kwh|
|Starting Method||DC 24V Electrical starting|
|Excite type||Brushless self-excited AVR regulation|
|Connecting type||3 phase 4 pole|
|Steady frequency change||0.50%|
|No load voltage||≥95%-105%|
|Insulation class||Class H|
Introduction Of Diesel Generator:
A Diesel Generator (DG) is a combination of diesel engine with electrical generator (often called an alternator) to generate electricity. DG sets are used in places that have no connection to power grid, and as emergency power-supply if the grid fails. In other words, DG sets remain the number one choice for standby and emergency power systems. DG sets are selected based on the electrical load they are intended to supply.
SCOPE OF SUPPLY
1. DIESEL ENGINE
1.1 Engine which includes wet type cylinder, direct injection combustion chamber, exhaust turbocharger, water cooling, electronic governor, etc.
1.2 Fuel system, which includes, fuel pump, strainers or filters, etc.
1.3 Air intake and exhaust system, which includes air filter, exhaust silencer, bellow, all intake and exhaust piping, cablings, instruments, valves and settings, etc.
1.4 Cooling system, which includes radiator with water level alarm and indicator, thermostatic switch, thermostatic heater, engine shaft mounted fan, all interconnecting piping, cablings, instruments, valves and settings, etc.
1.5 Lubricating system includes pumps, oil sumps, oil strainers and filters, all interconnecting piping, instruments, valves and settings, etc.
1.6 Starting system, which includes 2 sets of batteries, a set of AC charger, and interconnecting piping, cablings, instrument, valves and settings, etc.
2. AC SYNCHRONOUS GENERATOR
2.1 Generator, which includes exciter, rectifier, AVR, shaft mounted fan if required.
2.2 All interconnecting piping, cablings, instruments, valves and settings, etc.
3. COUPLINGS AND GUARD
3.2 Coupling Guard
4. CONTROL PANEL
4.1 Local automatic control panel
5.1 Common base plate
6.1 Generator Set Installation Manual
6.2 Generator Set Operation and Maintenance Manual
6.3 Generator Set Control Panel Manual
6.4 Engine Manual and Quality File
6.5 Alternator Manual and Quality File
6.6 Factory Acceptant Test Report