Wave distortion: <10%
Voltage fluctuation: <0.5%
Voltage / frequency fluctuation: <=0.5%
AVR self-regulated, voltage regulation rate: <=+- 1%
Radio interference restraining accords with stipulation of VDE0875-N and ISO8528
Key start / auto start
Monitoring meters: Current; Frequency; Wire Voltage; Genset KVA; Genset KW; Output
Capacity; Output KW.H; Power Factor.
Warning/Shutdown: Alternator Under/Over Volts, Frequency; Under/Over Speed; Low Oil Pressure; High Engine Temp; High/Low Battery Volts; Over Current; Earth Fault Shutdown.
SCOPE OF SUPPLY
1. DIESEL ENGINE
1.1 Engine which includes wet type cylinder, direct injection combustion chamber, exhaust turbocharger, water cooling, electronic governor, etc.
1.2 Fuel system, which includes, fuel pump, strainers or filters, etc.
1.3 Air intake and exhaust system, which includes air filter, exhaust silencer, bellow, all intake and exhaust piping, cablings, instruments, valves and settings, etc.
1.4 Cooling system, which includes radiator with water level alarm and indicator, thermostatic switch, thermostatic heater, engine shaft mounted fan, all interconnecting piping, cablings, instruments, valves and settings, etc.
1.5 Lubricating system includes pumps, oil sumps, oil strainers and filters, all interconnecting piping, instruments, valves and settings, etc.
1.6 Starting system, which includes 2 sets of batteries, a set of AC charger, and interconnecting piping, cablings, instrument, valves and settings, etc.
2. AC SYNCHRONOUS GENERATOR
2.1 Generator, which includes exciter, rectifier, AVR, shaft mounted fan if required.
2.2 All interconnecting piping, cablings, instruments, valves and settings, etc.
3. COUPLINGS AND GUARD
3.2 Coupling Guard
4. CONTROL PANEL
4.1 Local automatic control panel
5.1 Common base plate
6.1 Generator Set Installation Manual
6.2 Generator Set Operation and Maintenance Manual