Every generator set is subjected to a comprehensive test program which includes 25% load, 50% load, 75% load, 100% load, 110% load and the checking, proving of all control and safety shut-down function.
Equipped with battery charger and 24V high performance maintenance-free lead-acid starting batteries and connecting with cables.
Equipped with industrial silencer and flexible exhaust hose.
Equipped with 8-hours operation base tank.
Equipped with CHNT MCCB circuit breaker.
Designed to comply with ISO 8528/GB2820.
Powered by Cummins engine and coupled with Leory Somer alternator.
Genset rated power
280KW / 350KVA
230V / 400V (adjustable)
3 phase 4 wire
Closed cycle water-cooled with fan, water tank
Overall dimension (L×W×H) mm
6 cylinders vertical in line, 4 stroke, turbocharged
Engine cooling method
Speed governing system
Electronic speed governor
By 24V batteries
Engine filter system
Dry type air filter ,fuel filter, oil filter, water filter
100% Load fuel consumption (litre/h)
Brushless self-excited AVR regulation
3 phase 4 pole
Steady frequency change
No load voltage
Key start / auto start
Monitoring meters: Current; Frequency; Wire Voltage; Genset KVA; Genset KW; Output
Capacity; Output KW.H; Power Factor.
Warning/Shutdown: Alternator Under/Over Volts, Frequency; Under/Over Speed; Low Oil Pressure; High Engine Temp; High/Low Battery Volts; Over Current; Earth Fault Shutdown.
INSPECTION AND TEST
1.1 Each engine shall be tested at manufacturer’s workshop to certify the engine output and fuel consumption in accordance with the site operating condition specified by purchaser on the specification datasheet.
1.2 All relevant information drawings pertinent to the testing and test procedure shall be transmitted to the purchaser in advance of the test date notification.
1.3 The purchaser shall call for additional testing if test results are unsatisfactory or marginal. Any equipment rejected shall be repaired or replaced to the purchaser’s satisfaction and tests shall be repeated.
1.4 Any unsatisfactory material, equipment, installation, or workmanship shall be replaced or repaired to the purchasers satisfaction at the manufacturer’s cost.
1.5 The engine and generator shall be tested individually in accordance with relevant standards specified above.
1.6 The completed and individually tested engine and generator shall be assembled onto the base plate with all auxiliaries, instruments and controls for a complete test of the generator set.